ENB Region 7 Completed Applications 10/09/2013
City of Oneida
109 N Main St
Oneida, NY 13421
Oneida - C STP
387 Harden St
Oneida, NY 13421 -1129
Permit(s) Applied for:
Article 17 Titles 7 & 8 Municipal SPDES - Surface Discharge
Project is Located:
Oneida, Madison County
The Department of Environmental Conservation (DEC) has prepared a draft permit and has made a tentative determination to issue a renewal to State Pollutant Discharge Elimination Systems (SPDES) permit (NY#0026956). The City of Oneida Sewage Treatment Plant has a design flow of 3.75 mgd. The facility discharges treated wastewater to Oneida Creek, a class C water. Part of the treated wastewater is used in the Golf Course which is classified as groundwater discharge. Treatment at the plant consists of grit removal, primary settling tanks, aeration tanks, clarifiers, chlorination and dechlorination tanks, and a filtration unit. Sludge is treated with an anaerobic digester and a belt press then sent to landfill. The draft permit details known and possible Sanitary Sewer Overflows (SSOs) within the collection system. Bypass from these outfalls is prohibited expect when bypass is necessary to prevent loss of life, personal injury, public health hazard or sever property damage and there is no feasible alternative to the bypass. These SSOs are identified as Outfalls 002 and 005. No treatment is provided for these outfalls.
DEC proposes to incorporate the following modifications to this permit: -to include a quality based effluent limit (WQBEL) for Total Residual Chlorine (TRC) which is more stringent limit that the TRC limit in the current permit. The draft permit includes a TRC compliance schedule with an interim TRC limit such that the permittee can get a reasonable time to upgrade its plant to comply the proposed limit. -Outfall 003 has been removed since it is closed. -Reporting requirements for bypass Outfalls 002 and 005 have been added. -A short term, high intensity monitoring requirement for zinc has been added. -A Mercury Minimization Plan has been added. -Whole Effluent Toxicity testing requirements have been added. -A monitoring requirement for Dissolved Oxygen has been added.
Availability of Application Documents:
State Environmental Quality Review (SEQR) Determination:
Project is not subject to SEQR because it is a Type II action.
SEQR Lead Agency: None Designated
State Historic Preservation Act (SHPA) Determination:
Opportunity for Public Comment:
Comments on this project must be submitted in writing to the Contact Person no later than Nov 08, 2013.
Albany, NY 12233